Specifications and Features:
250 amp inverter battery breaker, 2 separate 60 amp AC inputs for generator and utility, 120 amp AC bypass switch, knockouts for up to seven din rail mount breakers, including the DCGFP63 DC or AC Din Rail breakers and 12 panel mount breakers or DC-GFP80 breakers. Massive tin plated copper bus bars directly connect to the XW’s battery terminals, bus bars for AC inputs, AC output, neutral, ground, PV + in, PV- in, Bat +, Bat-, 500 amp shunt, metal dead front behind the reversible door, Charge controllers mount to either side or both sides at once for dual controllers. (Note: The XW 60 amp controller can mount on the Right side only do to there isolated communications compartment) The XW MPPT controller requires no mounting bracket. FM60, FM80 and Classic require Right or Left E-Panel charge control mounting brackets. Right hand bracket furnished standard.