Specifications and Features:
175 amp inverter battery breaker, 2 separate 60 amp AC inputs for generator and utility, knockouts for up to seven din rail mount DC, DCGFP63 or AC breakers and 12 panel mount or DC-GFP80 breakers. Massive tin plated copper bus bars directly connect to the Schneider Electric XW’s battery terminals, bus bars for AC inputs, AC output, neutral, ground, PV + in, PV- in, Bat +, Bat-, 500 amp shunt, metal dead front behind the reversible door, Charge controllers mount to either side or both sides at once for dual controllers. AC bypass can be configured as input & output on/off as well as AC bypass. The XW MPPT controller requires no mounting bracket. FM60, FM80 and Classic require Right or Left E-Panel charge control mounting brackets. Right hand bracket furnished standard.
5 Year Manufacturer’s Warranty
Note: The Schneider Electric DC-GFP’s will not fit in the E-Panel. The MidNite Solar single circuit DC-GFP’s are designed for a single PV array. Two MidNite DC-GFP’s may be used to accommodate two arrays although the dual OutBack would work for dual arrays and dual controllers, cost less and takes up less room.